Is Drywall Necessary with Spray Foam Basement Insulation?
Originally published by: Journal of Light Construction — January 1, 2007
The following article was produced and published by the source linked to above, who is solely responsible for its content. SBC Magazine is publishing this story to raise awareness of information publicly available online and does not verify the accuracy of the author’s claims. As a consequence, SBC cannot vouch for the validity of any facts, claims or opinions made in the article.
Q.When the interior walls of an unfinished basement have been insulated with Icynene (or a similar spray-foam insulation), can the foam be left exposed, or does it have to be covered by a noncombustible material?
A.John Evans, codes and standards manager with Icynene, responds: Most building codes require that foam plastic insulation — including both rigid and open-cell low-density foam products — be separated from occupied living space (including basements) by an approved 15-minute thermal barrier.
While 1/2-inch gypsum board is recognized for this purpose by most codes, other less-common materials that can be used are sprayed-on cementitious coatings (A/D Fire Protection Systems,www.adfire.com ) and mineral-fiber coatings (American Sprayed Fibers, www.asfiusa.com). Before using a system not specifically mentioned by code, of course, it's always a good idea to consult first with your local building inspector.
In concealed spaces — like crawlspaces or unvented, conditioned attics — where there's no occupancy, an ignition barrier is usually required. Most building codes specifically approve 3/8-inch drywall for this purpose, but other options include spray-on intumescent paints — such as FF 88 (International Fire Resistant Systems, www.firefree.com ) — 1 1/2-inch mineral fiber, 1/4-inch wood structural panels, and .016-inch-thick corrosion-resistant metal.
In some unvented, conditioned attic applications, Icynene has been approved for use without an ignition barrier; for details, see Icynene's ICC-ES NER-420 report. Again, consult with your local code officials before choosing this approach or deciding on a specific ignition-barrier product or material.